&HEAD VERSION = 7300, TITLE = 'rit_60s-90s  talfa_300s  par_eq200s  t_max900s  fuoco_in_C7_corridoio' /
 
!! Scenario Configuration 
&TIME SIMULATION = 900 PRINT = 10 SMOKEVIEW = 10 SPREADSHEET = 10 / 
&INIT PRESSURE = 101325 RELATIVE_HUMIDITY = 50 INTERIOR_TEMPERATURE = 20 EXTERIOR_TEMPERATURE = 20 /
&MISC  LOWER_OXYGEN_LIMIT = 0.1 / 
 
!! Material Properties 
&MATL ID = 'STR 1' MATERIAL = 'pareti', 
      CONDUCTIVITY = 0.21 DENSITY = 900 SPECIFIC_HEAT = 1.09, THICKNESS = 0.2 EMISSIVITY = 0.9 /
&MATL ID = 'STR 2' MATERIAL = 'soffitti', 
      CONDUCTIVITY = 0.16 DENSITY = 550 SPECIFIC_HEAT = 1.66, THICKNESS = 0.3 EMISSIVITY = 0.9 /
&MATL ID = 'STR 3' MATERIAL = 'pavimenti', 
      CONDUCTIVITY = 1.35 DENSITY = 2394 SPECIFIC_HEAT = 1, THICKNESS = 0.3 EMISSIVITY = 0.9 /
&MATL ID = 'STR4' MATERIAL = 'parete c-gesso', 
      CONDUCTIVITY = 0.21 DENSITY = 900 SPECIFIC_HEAT = 1.09, THICKNESS = 0.03 EMISSIVITY = 0.9 /
&MATL ID = 'STR 5' MATERIAL = 'parete in vetro', 
      CONDUCTIVITY = 1 DENSITY = 2500 SPECIFIC_HEAT = 1, THICKNESS = 0.01 EMISSIVITY = 0.9 /
&MATL ID = 'STR 6' MATERIAL = 'target', 
      CONDUCTIVITY = 10 DENSITY = 1 SPECIFIC_HEAT = 1, THICKNESS = 0.001 EMISSIVITY = 0.9 /
 
!! Compartments 
&COMP ID = 'Comp 1'
      DEPTH = 9.7 HEIGHT = 2.7 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 21, 1.6, 2.8 GRID = 50, 50, 50 /
&COMP ID = 'Comp 2'
      DEPTH = 9.7 HEIGHT = 2.8 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR4' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 21, 1.6, 0 GRID = 50, 50, 50 /
&COMP ID = 'Comp 3'
      DEPTH = 9.7 HEIGHT = 2.7 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 28, 1.6, 2.8 GRID = 50, 50, 50 /
&COMP ID = 'Comp 4'
      DEPTH = 9.7 HEIGHT = 2.8 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR4' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 28, 1.6, 0 GRID = 50, 50, 50 /
&COMP ID = 'Comp 5'
      DEPTH = 9.7 HEIGHT = 2.7 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 35, 1.6, 2.8 GRID = 50, 50, 50 /
&COMP ID = 'Comp 6'
      DEPTH = 9.7 HEIGHT = 2.8 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR4' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 35, 1.6, 0 GRID = 50, 50, 50 /
&COMP ID = 'Comp 7'
      DEPTH = 9.7 HEIGHT = 2.7 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 42, 1.6, 2.8 GRID = 50, 50, 50 /
&COMP ID = 'Comp 8'
      DEPTH = 9.7 HEIGHT = 2.8 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR4' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 42, 1.6, 0 GRID = 50, 50, 50 /
&COMP ID = 'Comp 9'
      DEPTH = 0.9 HEIGHT = 6.5 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR4' FLOOR_MATL_ID = 'STR 3' SHAFT = .TRUE.
      ORIGIN = 21, 11.3, 0 GRID = 50, 50, 50 /
&COMP ID = 'Comp 10'
      DEPTH = 0.9 HEIGHT = 6.5 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR4' FLOOR_MATL_ID = 'STR 3' SHAFT = .TRUE.
      ORIGIN = 28, 11.3, 0 GRID = 50, 50, 50 /
&COMP ID = 'Comp 11'
      DEPTH = 0.9 HEIGHT = 6.5 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR4' FLOOR_MATL_ID = 'STR 3' SHAFT = .TRUE.
      ORIGIN = 35, 11.3, 0 GRID = 50, 50, 50 /
&COMP ID = 'Comp 12'
      DEPTH = 0.9 HEIGHT = 6.5 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR4' FLOOR_MATL_ID = 'STR 3' SHAFT = .TRUE.
      ORIGIN = 42, 11.3, 0 GRID = 50, 50, 50 /
&COMP ID = 'Comp 13'
      DEPTH = 1.6 HEIGHT = 4 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3' SHAFT = .TRUE.
      ORIGIN = 21, 0, 0 GRID = 50, 50, 50 /
&COMP ID = 'Comp 14'
      DEPTH = 1.6 HEIGHT = 4 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3' SHAFT = .TRUE.
      ORIGIN = 28, 0, 0 GRID = 50, 50, 50 /
&COMP ID = 'Comp 15'
      DEPTH = 1.6 HEIGHT = 4 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3' SHAFT = .TRUE.
      ORIGIN = 35, 0, 0 GRID = 50, 50, 50 /
&COMP ID = 'Comp 16'
      DEPTH = 1.6 HEIGHT = 4 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3' SHAFT = .TRUE.
      ORIGIN = 42, 0, 0 GRID = 50, 50, 50 /
&COMP ID = 'Comp 17'
      DEPTH = 4 HEIGHT = 2.8 WIDTH = 4 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3' SHAFT = .TRUE.
      ORIGIN = 49, 8.2, 0 GRID = 50, 50, 50 /
&COMP ID = 'Comp 18'
      DEPTH = 6.6 HEIGHT = 2.8 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 49, 1.6, 0 GRID = 50, 50, 50 /
&COMP ID = 'Comp 19'
      DEPTH = 9.7 HEIGHT = 2.7 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 49, 1.6, 2.8 GRID = 50, 50, 50 /
&COMP ID = 'Comp 20'
      DEPTH = 1.6 HEIGHT = 4 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3' SHAFT = .TRUE.
      ORIGIN = 49, 0, 0 GRID = 50, 50, 50 /
&COMP ID = 'Comp 21'
      DEPTH = 0.9 HEIGHT = 3.7 WIDTH = 3 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3' SHAFT = .TRUE.
      ORIGIN = 49, 11.3, 2.8 GRID = 50, 50, 50 /
&COMP ID = 'Comp 22'
      DEPTH = 10 HEIGHT = 2.7 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 21, 12.2, 2.8 GRID = 50, 50, 50 /
&COMP ID = 'Comp 23'
      DEPTH = 10 HEIGHT = 2.7 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 28, 12.2, 2.8 GRID = 50, 50, 50 /
&COMP ID = 'Comp 24'
      DEPTH = 10 HEIGHT = 2.7 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 35, 12.2, 2.8 GRID = 50, 50, 50 /
&COMP ID = 'Comp 25'
      DEPTH = 10 HEIGHT = 2.7 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 42, 12.2, 2.8 GRID = 50, 50, 50 /
&COMP ID = 'Comp 26'
      DEPTH = 10 HEIGHT = 2.7 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 49, 12.2, 2.8 GRID = 50, 50, 50 /
&COMP ID = 'Comp 27'
      DEPTH = 10 HEIGHT = 2.8 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR4' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 21, 12.2, 0 GRID = 50, 50, 50 /
&COMP ID = 'Comp 28'
      DEPTH = 10 HEIGHT = 2.8 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR4' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 28, 12.2, 0 GRID = 50, 50, 50 /
&COMP ID = 'Comp 29'
      DEPTH = 10 HEIGHT = 2.8 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR4' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 35, 12.2, 0 GRID = 50, 50, 50 /
&COMP ID = 'Comp 30'
      DEPTH = 10 HEIGHT = 2.8 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR4' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 42, 12.2, 0 GRID = 50, 50, 50 /
&COMP ID = 'Comp 31'
      DEPTH = 10 HEIGHT = 2.8 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 49, 12.2, 0 GRID = 50, 50, 50 /
&COMP ID = 'Comp 32'
      DEPTH = 1.3 HEIGHT = 4 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3' SHAFT = .TRUE.
      ORIGIN = 21, 22.2, 0 GRID = 50, 50, 50 /
&COMP ID = 'Comp 33'
      DEPTH = 1.3 HEIGHT = 4 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3' SHAFT = .TRUE.
      ORIGIN = 28, 22.2, 0 GRID = 50, 50, 50 /
&COMP ID = 'Comp 34'
      DEPTH = 1.3 HEIGHT = 4 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3' SHAFT = .TRUE.
      ORIGIN = 35, 22.2, 0 GRID = 50, 50, 50 /
&COMP ID = 'Comp 35'
      DEPTH = 1.3 HEIGHT = 4 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3' SHAFT = .TRUE.
      ORIGIN = 42, 22.2, 0 GRID = 50, 50, 50 /
&COMP ID = 'Comp 36'
      DEPTH = 1.3 HEIGHT = 4 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3' SHAFT = .TRUE.
      ORIGIN = 49, 22.2, 0 GRID = 50, 50, 50 /
&COMP ID = 'Comp 37'
      DEPTH = 0.9 HEIGHT = 3.7 WIDTH = 4 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3' SHAFT = .TRUE.
      ORIGIN = 52, 11.3, 2.8 GRID = 50, 50, 50 /
&COMP ID = 'C1_P2_S1'
      DEPTH = 4 HEIGHT = 2.8 WIDTH = 3 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 53, 8.2, 0 GRID = 50, 50, 50 /
&COMP ID = 'C6_C7_P2_7'
      DEPTH = 4.8 HEIGHT = 2.8 WIDTH = 1.8 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 5' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 19.2, 6.5, 0 GRID = 50, 50, 50 /
&COMP ID = 'C6_C7_P2_6'
      DEPTH = 4.8 HEIGHT = 2.8 WIDTH = 1.8 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 7, 6.5, 0 GRID = 50, 50, 50 /
&COMP ID = 'C6_C7_P2_5'
      DEPTH = 5 HEIGHT = 2.8 WIDTH = 14 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 7, 18.5, 0 GRID = 50, 50, 50 /
&COMP ID = 'C6_C7_P2_4'
      DEPTH = 6.3 HEIGHT = 2.8 WIDTH = 14 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 7, 12.2, 0 GRID = 50, 50, 50 /
&COMP ID = 'C6_C7_P2_3'
      DEPTH = 4.8 HEIGHT = 2.8 WIDTH = 10.4 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 5' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 8.8, 6.5, 0 GRID = 50, 50, 50 /
&COMP ID = 'C6_C7_P2_2'
      DEPTH = 2 HEIGHT = 2.8 WIDTH = 14 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 7, 4.5, 0 GRID = 50, 50, 50 /
&COMP ID = 'C6_C7_P2_1'
      DEPTH = 4.5 HEIGHT = 2.8 WIDTH = 14 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 7, 0, 0 GRID = 50, 50, 50 /
&COMP ID = 'C6_C7_W_P3'
      DEPTH = 11.3 HEIGHT = 2.7 WIDTH = 14 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 7, 12.2, 2.8 GRID = 50, 50, 50 /
&COMP ID = 'C6_C7_E_P3'
      DEPTH = 11.3 HEIGHT = 2.7 WIDTH = 14 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 7, 0, 2.8 GRID = 50, 50, 50 /
&COMP ID = 'C6_C7_C'
      DEPTH = 0.9 HEIGHT = 6.5 WIDTH = 14 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3' SHAFT = .TRUE.
      ORIGIN = 7, 11.3, 0 GRID = 50, 50, 50 /
&COMP ID = 'C8_W_P2'
      DEPTH = 11.3 HEIGHT = 2.8 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 0, 12.2, 0 GRID = 50, 50, 50 /
&COMP ID = 'Scala S2'
      DEPTH = 4 HEIGHT = 2.8 WIDTH = 4 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3' SHAFT = .TRUE.
      ORIGIN = 3, 8.2, 0 GRID = 50, 50, 50 /
&COMP ID = 'Camino S2'
      DEPTH = 0.9 HEIGHT = 3.7 WIDTH = 4 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3' SHAFT = .TRUE.
      ORIGIN = 3, 11.3, 2.8 GRID = 50, 50, 50 /
&COMP ID = 'C8_E_P2'
      DEPTH = 8.2 HEIGHT = 2.8 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 0, 0, 0 GRID = 50, 50, 50 /
&COMP ID = 'C8_P2_S2'
      DEPTH = 4 HEIGHT = 2.8 WIDTH = 3 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 0, 8.2, 0 GRID = 50, 50, 50 /
&COMP ID = 'C8_E_P3'
      DEPTH = 11.3 HEIGHT = 2.8 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 0, 0, 2.8 GRID = 50, 50, 50 /
&COMP ID = 'C8_W_P3'
      DEPTH = 11.3 HEIGHT = 2.7 WIDTH = 7 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3'
      ORIGIN = 0, 12.2, 2.8 GRID = 50, 50, 50 /
&COMP ID = 'C8_C_P3'
      DEPTH = 0.9 HEIGHT = 3.7 WIDTH = 3 CEILING_MATL_ID = 'STR 2' WALL_MATL_ID = 'STR 1' FLOOR_MATL_ID = 'STR 3' SHAFT = .TRUE.
      ORIGIN = 0, 11.3, 2.8 GRID = 50, 50, 50 /
 
!! Wall Vents
&VENT TYPE = 'WALL' ID = 'WallVent_1' COMP_IDS = 'Comp 2', 'Comp 9' TOP = 2.1, BOTTOM = 0, WIDTH = 0.8
  FACE = 'REAR' OFFSET = 3.1 /
&VENT TYPE = 'WALL' ID = 'WallVent_2' COMP_IDS = 'Comp 4', 'Comp 6' TOP = 2.8, BOTTOM = 0, WIDTH = 8
  FACE = 'RIGHT' OFFSET = 1 /
&VENT TYPE = 'WALL' ID = 'WallVent_3' COMP_IDS = 'Comp 4', 'Comp 10' TOP = 2.1, BOTTOM = 0, WIDTH = 0.8
  FACE = 'REAR' OFFSET = 3.1 /
&VENT TYPE = 'WALL' ID = 'WallVent_4' COMP_IDS = 'Comp 6', 'Comp 11' TOP = 2.1, BOTTOM = 0, WIDTH = 0.8
  FACE = 'REAR' OFFSET = 3.1 /
&VENT TYPE = 'WALL' ID = 'WallVent_5' COMP_IDS = 'Comp 8', 'Comp 12' TOP = 2.1, BOTTOM = 0, WIDTH = 1.2
  FACE = 'REAR' OFFSET = 3.1 /
&VENT TYPE = 'WALL' ID = 'WallVent_6' COMP_IDS = 'Comp 8', 'Comp 18' TOP = 2.8, BOTTOM = 0, WIDTH = 5
  FACE = 'RIGHT' OFFSET = 1 /
&VENT TYPE = 'WALL' ID = 'WallVent_7' COMP_IDS = 'Comp 1', 'Comp 3' TOP = 2.1, BOTTOM = 0, WIDTH = 1.2
  FACE = 'RIGHT' OFFSET = 2 /
&VENT TYPE = 'WALL' ID = 'WallVent_8' COMP_IDS = 'Comp 3', 'Comp 5' TOP = 2.1, BOTTOM = 0, WIDTH = 1.2
  FACE = 'RIGHT' OFFSET = 2 /
&VENT TYPE = 'WALL' ID = 'WallVent_9' COMP_IDS = 'Comp 5', 'Comp 7' TOP = 2.1, BOTTOM = 0, WIDTH = 1.2
  FACE = 'RIGHT' OFFSET = 2 /
&VENT TYPE = 'WALL' ID = 'WallVent_10' COMP_IDS = 'Comp 7', 'Comp 19' TOP = 2.1, BOTTOM = 0, WIDTH = 1.2
  FACE = 'RIGHT' OFFSET = 2 /
&VENT TYPE = 'WALL' ID = 'WallVent_11' COMP_IDS = 'Comp 2', 'Comp 13' TOP = 2.8, BOTTOM = 0, WIDTH = 6
  FACE = 'REAR' OFFSET = 0.5 /
&VENT TYPE = 'WALL' ID = 'WallVent_12' COMP_IDS = 'Comp 4', 'Comp 14' TOP = 2.8, BOTTOM = 0, WIDTH = 6
  FACE = 'REAR' OFFSET = 0.5 /
&VENT TYPE = 'WALL' ID = 'WallVent_13' COMP_IDS = 'Comp 6', 'Comp 15' TOP = 2.8, BOTTOM = 0, WIDTH = 6
  FACE = 'REAR' OFFSET = 0.5 /
&VENT TYPE = 'WALL' ID = 'WallVent_14' COMP_IDS = 'Comp 8', 'Comp 16' TOP = 2.8, BOTTOM = 0, WIDTH = 6
  FACE = 'REAR' OFFSET = 0.5 /
&VENT TYPE = 'WALL' ID = 'WallVent_15' COMP_IDS = 'Comp 18', 'Comp 20' TOP = 2.8, BOTTOM = 0, WIDTH = 6
  FACE = 'REAR' OFFSET = 0.5 /
&VENT TYPE = 'WALL' ID = 'WallVent_16' COMP_IDS = 'Comp 25', 'Comp 26' TOP = 2.1, BOTTOM = 0, WIDTH = 1.2
  FACE = 'RIGHT' OFFSET = 0.1 /
&VENT TYPE = 'WALL' ID = 'WallVent_17' COMP_IDS = 'Comp 9', 'Comp 10' TOP = 2.8, BOTTOM = 0, WIDTH = 0.9
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'RIGHT' OFFSET = 0 /
&VENT TYPE = 'WALL' ID = 'WallVent_18' COMP_IDS = 'Comp 10', 'Comp 11' TOP = 2.8, BOTTOM = 0, WIDTH = 0.9
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'RIGHT' OFFSET = 0 /
&VENT TYPE = 'WALL' ID = 'WallVent_19' COMP_IDS = 'Comp 11', 'Comp 12' TOP = 2.8, BOTTOM = 0, WIDTH = 0.9
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'RIGHT' OFFSET = 0 /
&VENT TYPE = 'WALL' ID = 'WallVent_20' COMP_IDS = 'Comp 12', 'Comp 17' TOP = 2.8, BOTTOM = 0, WIDTH = 0.9
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'RIGHT' OFFSET = 0 /
&VENT TYPE = 'WALL' ID = 'WallVent_21' COMP_IDS = 'Comp 9', 'Comp 27' TOP = 2.1, BOTTOM = 0, WIDTH = 0.8
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'REAR' OFFSET = 5.5 /
&VENT TYPE = 'WALL' ID = 'WallVent_22' COMP_IDS = 'Comp 10', 'Comp 28' TOP = 2.1, BOTTOM = 0, WIDTH = 0.8
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'REAR' OFFSET = 5.5 /
&VENT TYPE = 'WALL' ID = 'WallVent_23' COMP_IDS = 'Comp 12', 'Comp 30' TOP = 2.1, BOTTOM = 0, WIDTH = 0.8
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'REAR' OFFSET = 0.1 /
&VENT TYPE = 'WALL' ID = 'WallVent_24' COMP_IDS = 'Comp 28', 'Comp 29' TOP = 2.7, BOTTOM = 0, WIDTH = 8
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'RIGHT' OFFSET = 1 /
&VENT TYPE = 'WALL' ID = 'WallVent_25' COMP_IDS = 'Comp 29', 'Comp 30' TOP = 2.7, BOTTOM = 0, WIDTH = 1.2
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'RIGHT' OFFSET = 4.4 /
&VENT TYPE = 'WALL' ID = 'WallVent_26' COMP_IDS = 'Comp 30', 'Comp 31' TOP = 2.7, BOTTOM = 0, WIDTH = 6
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'RIGHT' OFFSET = 2 /
&VENT TYPE = 'WALL' ID = 'WallVent_27' COMP_IDS = 'Comp 27', 'Comp 32' TOP = 2.8, BOTTOM = 0, WIDTH = 6
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'REAR' OFFSET = 0.5 /
&VENT TYPE = 'WALL' ID = 'WallVent_28' COMP_IDS = 'Comp 28', 'Comp 33' TOP = 2.8, BOTTOM = 0, WIDTH = 6
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'REAR' OFFSET = 0.5 /
&VENT TYPE = 'WALL' ID = 'WallVent_29' COMP_IDS = 'Comp 29', 'Comp 34' TOP = 2.8, BOTTOM = 0, WIDTH = 6
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'REAR' OFFSET = 0.5 /
&VENT TYPE = 'WALL' ID = 'WallVent_30' COMP_IDS = 'Comp 30', 'Comp 35' TOP = 2.8, BOTTOM = 0, WIDTH = 6
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'REAR' OFFSET = 0.5 /
&VENT TYPE = 'WALL' ID = 'WallVent_31' COMP_IDS = 'Comp 31', 'Comp 36' TOP = 2.8, BOTTOM = 0, WIDTH = 6
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'REAR' OFFSET = 0.5 /
&VENT TYPE = 'WALL' ID = 'WallVent_32' COMP_IDS = 'Comp 1', 'Comp 9' TOP = 2.2, BOTTOM = 1.7, WIDTH = 1.8
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 1 FACE = 'REAR' OFFSET = 4 /
&VENT TYPE = 'WALL' ID = 'WallVent_33' COMP_IDS = 'Comp 9', 'Comp 22' TOP = 5, BOTTOM = 4.5, WIDTH = 1.8
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 1 FACE = 'REAR' OFFSET = 4 /
&VENT TYPE = 'WALL' ID = 'WallVent_34' COMP_IDS = 'Comp 3', 'Comp 10' TOP = 2.2, BOTTOM = 1.7, WIDTH = 1.8
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 1 FACE = 'REAR' OFFSET = 4 /
&VENT TYPE = 'WALL' ID = 'WallVent_35' COMP_IDS = 'Comp 10', 'Comp 23' TOP = 5, BOTTOM = 4.5, WIDTH = 1.8
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 1 FACE = 'REAR' OFFSET = 4 /
&VENT TYPE = 'WALL' ID = 'WallVent_36' COMP_IDS = 'Comp 5', 'Comp 11' TOP = 2.2, BOTTOM = 1.7, WIDTH = 1.8
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 1 FACE = 'REAR' OFFSET = 4 /
&VENT TYPE = 'WALL' ID = 'WallVent_37' COMP_IDS = 'Comp 11', 'Comp 24' TOP = 5, BOTTOM = 4.5, WIDTH = 1.8
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 1 FACE = 'REAR' OFFSET = 4 /
&VENT TYPE = 'WALL' ID = 'WallVent_38' COMP_IDS = 'Comp 19', 'Comp 21' TOP = 2.2, BOTTOM = 1.7, WIDTH = 1
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 1 FACE = 'REAR' OFFSET = 1 /
&VENT TYPE = 'WALL' ID = 'WallVent_39' COMP_IDS = 'Comp 21', 'Comp 26' TOP = 2.2, BOTTOM = 1.7, WIDTH = 1
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 1 FACE = 'REAR' OFFSET = 1 /
&VENT TYPE = 'WALL' ID = 'WallVent_40' COMP_IDS = 'Comp 1', 'Comp 22' TOP = 2.1, BOTTOM = 0, WIDTH = 1.6
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'REAR' OFFSET = 1 /
&VENT TYPE = 'WALL' ID = 'WallVent_41' COMP_IDS = 'Comp 3', 'Comp 23' TOP = 2.1, BOTTOM = 0, WIDTH = 1.6
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'REAR' OFFSET = 1 /
&VENT TYPE = 'WALL' ID = 'WallVent_42' COMP_IDS = 'Comp 5', 'Comp 24' TOP = 2.1, BOTTOM = 0, WIDTH = 1.6
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'REAR' OFFSET = 1 /
&VENT TYPE = 'WALL' ID = 'WallVent_43' COMP_IDS = 'Comp 19', 'Comp 37' TOP = 2.1, BOTTOM = 0, WIDTH = 4
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'REAR' OFFSET = 3 /
&VENT TYPE = 'WALL' ID = 'WallVent_44' COMP_IDS = 'Comp 26', 'Comp 37' TOP = 2.1, BOTTOM = 0, WIDTH = 4
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'REAR' OFFSET = 0 /
&VENT TYPE = 'WALL' ID = 'WallVent_45' COMP_IDS = 'Comp 17', 'C1_P2_S1' TOP = 2.1, BOTTOM = 0, WIDTH = 1.2
  CRITERION = 'TIME' T = 0, 300, 301 F = 0.5, 0.5, 1 FACE = 'RIGHT' OFFSET = 2.7 /
&VENT TYPE = 'WALL' ID = 'WallVent_46' COMP_IDS = 'C1_P2_S1' 'OUTSIDE'  TOP = 2.1, BOTTOM = 0, WIDTH = 1.2
  CRITERION = 'TIME' T = 0, 300, 301 F = 0.5, 0.5, 1 FACE = 'RIGHT' OFFSET = 2.7 /
&VENT TYPE = 'WALL' ID = 'WallVent_47' COMP_IDS = 'Scala S2', 'C8_P2_S2' TOP = 2.1, BOTTOM = 0, WIDTH = 1.2
  CRITERION = 'TIME' T = 0, 300, 301 F = 0.5, 0.5, 1 FACE = 'LEFT' OFFSET = 2.7 /
&VENT TYPE = 'WALL' ID = 'WallVent_48' COMP_IDS = 'C8_P2_S2' 'OUTSIDE'  TOP = 2.1, BOTTOM = 0, WIDTH = 1.2
  CRITERION = 'TIME' T = 0, 300, 301 F = 0.5, 0.5, 1 FACE = 'LEFT' OFFSET = 2.7 /
&VENT TYPE = 'WALL' ID = 'WallVent_49' COMP_IDS = 'C8_W_P2', 'C8_P2_S2' TOP = 2.1, BOTTOM = 0, WIDTH = 1.2
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 1 FACE = 'FRONT' OFFSET = 0.5 /
&VENT TYPE = 'WALL' ID = 'WallVent_50' COMP_IDS = 'C8_E_P2', 'C8_P2_S2' TOP = 2.1, BOTTOM = 0, WIDTH = 1.2
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 1 FACE = 'REAR' OFFSET = 0.5 /
&VENT TYPE = 'WALL' ID = 'WallVent_51' COMP_IDS = 'Comp 13' 'OUTSIDE'  TOP = 2.5, BOTTOM = 0, WIDTH = 2.4
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'FRONT' OFFSET = 2.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_52' COMP_IDS = 'Comp 14' 'OUTSIDE'  TOP = 2.5, BOTTOM = 0, WIDTH = 2.4
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'FRONT' OFFSET = 2.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_53' COMP_IDS = 'Comp 15' 'OUTSIDE'  TOP = 2.5, BOTTOM = 0, WIDTH = 2.4
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'FRONT' OFFSET = 2.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_54' COMP_IDS = 'Comp 16' 'OUTSIDE'  TOP = 2.5, BOTTOM = 0, WIDTH = 2.4
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'FRONT' OFFSET = 2.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_55' COMP_IDS = 'Comp 20' 'OUTSIDE'  TOP = 2.5, BOTTOM = 0, WIDTH = 2.4
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'FRONT' OFFSET = 2.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_56' COMP_IDS = 'Comp 32' 'OUTSIDE'  TOP = 2.5, BOTTOM = 0, WIDTH = 2.4
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'REAR' OFFSET = 2.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_57' COMP_IDS = 'Comp 33' 'OUTSIDE'  TOP = 2.5, BOTTOM = 0, WIDTH = 2.4
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'REAR' OFFSET = 2.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_58' COMP_IDS = 'Comp 34' 'OUTSIDE'  TOP = 2.5, BOTTOM = 0, WIDTH = 2.4
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'REAR' OFFSET = 2.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_59' COMP_IDS = 'Comp 35' 'OUTSIDE'  TOP = 2.5, BOTTOM = 0, WIDTH = 2.4
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'REAR' OFFSET = 2.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_60' COMP_IDS = 'Comp 36' 'OUTSIDE'  TOP = 2.5, BOTTOM = 0, WIDTH = 2.4
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'REAR' OFFSET = 2.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_61' COMP_IDS = 'Comp 18' 'OUTSIDE'  TOP = 2.7, BOTTOM = 1.2, WIDTH = 1.5
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'RIGHT' OFFSET = 2.5 /
&VENT TYPE = 'WALL' ID = 'WallVent_62' COMP_IDS = 'Comp 31' 'OUTSIDE'  TOP = 2.7, BOTTOM = 1.2, WIDTH = 1.5
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'RIGHT' OFFSET = 4.2 /
&VENT TYPE = 'WALL' ID = 'WallVent_63' COMP_IDS = 'Comp 19' 'OUTSIDE'  TOP = 2.7, BOTTOM = 1.2, WIDTH = 1.5
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'RIGHT' OFFSET = 2.5 /
&VENT TYPE = 'WALL' ID = 'WallVent_64' COMP_IDS = 'Comp 26' 'OUTSIDE'  TOP = 2.7, BOTTOM = 1.2, WIDTH = 1.5
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'RIGHT' OFFSET = 4.2 /
&VENT TYPE = 'WALL' ID = 'WallVent_65' COMP_IDS = 'Comp 13' 'OUTSIDE'  TOP = 3.3, BOTTOM = 2.8, WIDTH = 2.4
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'FRONT' OFFSET = 2.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_66' COMP_IDS = 'Comp 14' 'OUTSIDE'  TOP = 3.3, BOTTOM = 2.8, WIDTH = 2.4
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'FRONT' OFFSET = 2.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_67' COMP_IDS = 'Comp 15' 'OUTSIDE'  TOP = 3.3, BOTTOM = 2.8, WIDTH = 2.4
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'FRONT' OFFSET = 2.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_68' COMP_IDS = 'Comp 16' 'OUTSIDE'  TOP = 3.3, BOTTOM = 2.8, WIDTH = 2.4
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'FRONT' OFFSET = 2.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_69' COMP_IDS = 'Comp 20' 'OUTSIDE'  TOP = 3.3, BOTTOM = 2.8, WIDTH = 2.4
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'FRONT' OFFSET = 2.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_70' COMP_IDS = 'Comp 32' 'OUTSIDE'  TOP = 3.3, BOTTOM = 2.8, WIDTH = 2.4
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'REAR' OFFSET = 2.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_71' COMP_IDS = 'Comp 33' 'OUTSIDE'  TOP = 3.3, BOTTOM = 2.8, WIDTH = 2.4
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'REAR' OFFSET = 2.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_72' COMP_IDS = 'Comp 34' 'OUTSIDE'  TOP = 3.3, BOTTOM = 2.8, WIDTH = 2.4
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'REAR' OFFSET = 2.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_73' COMP_IDS = 'Comp 35' 'OUTSIDE'  TOP = 3.3, BOTTOM = 2.8, WIDTH = 2.4
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'REAR' OFFSET = 2.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_74' COMP_IDS = 'Comp 36' 'OUTSIDE'  TOP = 3.3, BOTTOM = 2.8, WIDTH = 2.4
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'REAR' OFFSET = 2.3 /
&VENT TYPE = 'WALL' ID = 'abbaino_75' COMP_IDS = 'Comp 1' 'OUTSIDE'  TOP = 2.6, BOTTOM = 1.3, WIDTH = 1.7
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'FRONT' OFFSET = 2.6 /
&VENT TYPE = 'WALL' ID = 'abbaino_76' COMP_IDS = 'Comp 3' 'OUTSIDE'  TOP = 2.6, BOTTOM = 1.3, WIDTH = 1.7
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'FRONT' OFFSET = 2.6 /
&VENT TYPE = 'WALL' ID = 'abbaino_77' COMP_IDS = 'Comp 5' 'OUTSIDE'  TOP = 2.6, BOTTOM = 1.3, WIDTH = 1.7
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'FRONT' OFFSET = 2.6 /
&VENT TYPE = 'WALL' ID = 'abbaino_78' COMP_IDS = 'Comp 7' 'OUTSIDE'  TOP = 2.6, BOTTOM = 1.3, WIDTH = 1.7
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'FRONT' OFFSET = 2.6 /
&VENT TYPE = 'WALL' ID = 'abbaino_79' COMP_IDS = 'Comp 19' 'OUTSIDE'  TOP = 2.6, BOTTOM = 1.3, WIDTH = 1.7
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'FRONT' OFFSET = 2.6 /
&VENT TYPE = 'WALL' ID = 'abbaino_80' COMP_IDS = 'Comp 22' 'OUTSIDE'  TOP = 2.6, BOTTOM = 1.3, WIDTH = 1.7
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'REAR' OFFSET = 2.65 /
&VENT TYPE = 'WALL' ID = 'abbaino_81' COMP_IDS = 'Comp 23' 'OUTSIDE'  TOP = 2.6, BOTTOM = 1.3, WIDTH = 1.7
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'REAR' OFFSET = 2.65 /
&VENT TYPE = 'WALL' ID = 'abbaino_82' COMP_IDS = 'Comp 24' 'OUTSIDE'  TOP = 2.6, BOTTOM = 1.3, WIDTH = 1.7
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'REAR' OFFSET = 2.65 /
&VENT TYPE = 'WALL' ID = 'abbaino_83' COMP_IDS = 'Comp 25' 'OUTSIDE'  TOP = 2.6, BOTTOM = 1.3, WIDTH = 1.7
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'REAR' OFFSET = 2.65 /
&VENT TYPE = 'WALL' ID = 'abbaino_84' COMP_IDS = 'Comp 26' 'OUTSIDE'  TOP = 2.6, BOTTOM = 1.3, WIDTH = 1.7
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'REAR' OFFSET = 2.65 /
&VENT TYPE = 'WALL' ID = 'WallVent_85' COMP_IDS = 'C6_C7_P2_1' 'OUTSIDE'  TOP = 2.8, BOTTOM = 0, WIDTH = 2.4
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'FRONT' OFFSET = 2.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_86' COMP_IDS = 'C6_C7_P2_1' 'OUTSIDE'  TOP = 2.8, BOTTOM = 0, WIDTH = 2.4
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'FRONT' OFFSET = 9.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_87' COMP_IDS = 'C6_C7_P2_5' 'OUTSIDE'  TOP = 2.8, BOTTOM = 0, WIDTH = 2.4
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'REAR' OFFSET = 2.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_88' COMP_IDS = 'C6_C7_P2_5' 'OUTSIDE'  TOP = 2.8, BOTTOM = 0, WIDTH = 2.4
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'REAR' OFFSET = 9.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_89' COMP_IDS = 'C6_C7_C', 'Scala S2' TOP = 2.8, BOTTOM = 0, WIDTH = 0.9
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'LEFT' OFFSET = 0 /
&VENT TYPE = 'WALL' ID = 'WallVent_90' COMP_IDS = 'Comp 9', 'C6_C7_C' TOP = 2.8, BOTTOM = 0, WIDTH = 0.9
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'LEFT' OFFSET = 0 /
&VENT TYPE = 'WALL' ID = 'WallVent_91' COMP_IDS = 'Comp 27', 'C6_C7_P2_4' TOP = 2.1, BOTTOM = 0, WIDTH = 0.9
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'LEFT' OFFSET = 2 /
&VENT TYPE = 'WALL' ID = 'WallVent_92' COMP_IDS = 'Comp 2', 'C6_C7_P2_2' TOP = 2.8, BOTTOM = 0, WIDTH = 1.2
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'LEFT' OFFSET = 3.5 /
&VENT TYPE = 'WALL' ID = 'WallVent_93' COMP_IDS = 'Comp 2', 'C6_C7_P2_7' TOP = 2.8, BOTTOM = 0, WIDTH = 2
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'LEFT' OFFSET = 5.5 /
&VENT TYPE = 'WALL' ID = 'WallVent_94' COMP_IDS = 'C6_C7_P2_6', 'C6_C7_P2_2' TOP = 2.8, BOTTOM = 0, WIDTH = 1.8
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'FRONT' OFFSET = 0 /
&VENT TYPE = 'WALL' ID = 'WallVent_95' COMP_IDS = 'C6_C7_P2_6', 'C6_C7_C' TOP = 2.8, BOTTOM = 0, WIDTH = 1.8
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'REAR' OFFSET = 0 /
&VENT TYPE = 'WALL' ID = 'WallVent_96' COMP_IDS = 'C6_C7_P2_7', 'C6_C7_P2_2' TOP = 2.8, BOTTOM = 0, WIDTH = 1.8
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'FRONT' OFFSET = 0 /
&VENT TYPE = 'WALL' ID = 'WallVent_97' COMP_IDS = 'C6_C7_P2_7', 'C6_C7_C' TOP = 2.8, BOTTOM = 0, WIDTH = 1.8
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'REAR' OFFSET = 0 /
&VENT TYPE = 'WALL' ID = 'WallVent_98' COMP_IDS = 'C6_C7_P2_2', 'C6_C7_P2_1' TOP = 2.1, BOTTOM = 0, WIDTH = 0.9
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'REAR' OFFSET = 4 /
&VENT TYPE = 'WALL' ID = 'WallVent_99' COMP_IDS = 'C6_C7_P2_2', 'C6_C7_P2_1' TOP = 2.1, BOTTOM = 0, WIDTH = 0.9
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'REAR' OFFSET = 8 /
&VENT TYPE = 'WALL' ID = 'WallVent_100' COMP_IDS = 'C6_C7_P2_2', 'C6_C7_P2_1' TOP = 2.1, BOTTOM = 0, WIDTH = 0.9
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'REAR' OFFSET = 12 /
&VENT TYPE = 'WALL' ID = 'WallVent_101' COMP_IDS = 'C6_C7_P2_3', 'C6_C7_P2_2' TOP = 2.1, BOTTOM = 0, WIDTH = 0.9
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'REAR' OFFSET = 2.5 /
&VENT TYPE = 'WALL' ID = 'WallVent_102' COMP_IDS = 'C6_C7_P2_3', 'C6_C7_P2_2' TOP = 2.1, BOTTOM = 0, WIDTH = 0.9
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'REAR' OFFSET = 8 /
&VENT TYPE = 'WALL' ID = 'WallVent_103' COMP_IDS = 'C6_C7_P2_5', 'C6_C7_P2_4' TOP = 2.1, BOTTOM = 0, WIDTH = 0.9
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'FRONT' OFFSET = 0.5 /
&VENT TYPE = 'WALL' ID = 'WallVent_104' COMP_IDS = 'C6_C7_P2_5', 'C6_C7_P2_4' TOP = 2.1, BOTTOM = 0, WIDTH = 0.9
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'FRONT' OFFSET = 7 /
&VENT TYPE = 'WALL' ID = 'WallVent_105' COMP_IDS = 'C6_C7_P2_5', 'C6_C7_P2_4' TOP = 2.1, BOTTOM = 0, WIDTH = 0.9
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'FRONT' OFFSET = 12 /
&VENT TYPE = 'WALL' ID = 'WallVent_106' COMP_IDS = 'C6_C7_P2_3', 'C6_C7_C' TOP = 2.8, BOTTOM = 0, WIDTH = 10.4
  CRITERION = 'TIME' T = 0, 900 F = 0, 0 FACE = 'REAR' OFFSET = 0 /
&VENT TYPE = 'WALL' ID = 'WallVent_107' COMP_IDS = 'C8_W_P2' 'OUTSIDE'  TOP = 2.8, BOTTOM = 0, WIDTH = 2.4
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'REAR' OFFSET = 2.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_108' COMP_IDS = 'C8_E_P2' 'OUTSIDE'  TOP = 2.8, BOTTOM = 0, WIDTH = 2.4
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'FRONT' OFFSET = 2.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_109' COMP_IDS = 'C6_C7_P2_4', 'C8_W_P2' TOP = 2.1, BOTTOM = 0, WIDTH = 3
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'RIGHT' OFFSET = 0 /
&VENT TYPE = 'WALL' ID = 'WallVent_110' COMP_IDS = 'C8_E_P3' 'OUTSIDE'  TOP = 2.6, BOTTOM = 1.3, WIDTH = 1.7
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'FRONT' OFFSET = 2.65 /
&VENT TYPE = 'WALL' ID = 'WallVent_111' COMP_IDS = 'C6_C7_E_P3' 'OUTSIDE'  TOP = 2.6, BOTTOM = 1.3, WIDTH = 1.7
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'FRONT' OFFSET = 2.6 /
&VENT TYPE = 'WALL' ID = 'WallVent_112' COMP_IDS = 'C6_C7_E_P3' 'OUTSIDE'  TOP = 2.6, BOTTOM = 1.3, WIDTH = 1.7
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'FRONT' OFFSET = 9.6 /
&VENT TYPE = 'WALL' ID = 'WallVent_113' COMP_IDS = 'C6_C7_W_P3' 'OUTSIDE'  TOP = 2.6, BOTTOM = 1.3, WIDTH = 1.7
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'REAR' OFFSET = 2.6 /
&VENT TYPE = 'WALL' ID = 'WallVent_114' COMP_IDS = 'C6_C7_W_P3' 'OUTSIDE'  TOP = 2.6, BOTTOM = 1.3, WIDTH = 1.7
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'REAR' OFFSET = 9.6 /
&VENT TYPE = 'WALL' ID = 'WallVent_115' COMP_IDS = 'C6_C7_E_P3', 'C6_C7_C' TOP = 2.5, BOTTOM = 2, WIDTH = 1.6
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 1 FACE = 'REAR' OFFSET = 2.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_116' COMP_IDS = 'C6_C7_E_P3', 'C6_C7_C' TOP = 2.5, BOTTOM = 2, WIDTH = 1.6
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 1 FACE = 'REAR' OFFSET = 9.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_117' COMP_IDS = 'C6_C7_W_P3', 'C6_C7_C' TOP = 2.5, BOTTOM = 2, WIDTH = 1.6
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 1 FACE = 'FRONT' OFFSET = 2.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_118' COMP_IDS = 'C6_C7_W_P3', 'C6_C7_C' TOP = 2.5, BOTTOM = 2, WIDTH = 1.6
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 1 FACE = 'FRONT' OFFSET = 9.3 /
&VENT TYPE = 'WALL' ID = 'WallVent_119' COMP_IDS = 'C8_W_P3' 'OUTSIDE'  TOP = 2.6, BOTTOM = 1.3, WIDTH = 1.7
  CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 FACE = 'REAR' OFFSET = 2.65 /
&VENT TYPE = 'WALL' ID = 'WallVent_120' COMP_IDS = 'C6_C7_E_P3', 'C8_W_P3' TOP = 2.1, BOTTOM = 0, WIDTH = 0.9
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'RIGHT' OFFSET = 5.2 /
&VENT TYPE = 'WALL' ID = 'WallVent_121' COMP_IDS = 'C8_W_P3', 'C8_C_P3' TOP = 2.7, BOTTOM = 0, WIDTH = 1.8
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'REAR' OFFSET = 0.6 /
&VENT TYPE = 'WALL' ID = 'WallVent_122' COMP_IDS = 'C8_E_P3', 'C8_C_P3' TOP = 2.7, BOTTOM = 0, WIDTH = 1.8
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'FRONT' OFFSET = 0.6 /
&VENT TYPE = 'WALL' ID = 'WallVent_123' COMP_IDS = 'C6_C7_P2_4', 'C6_C7_C' TOP = 2.8, BOTTOM = 0, WIDTH = 14
  CRITERION = 'TIME' T = 0, 900 F = 1, 1 FACE = 'REAR' OFFSET = 0 /
 
!! Ceiling and Floor Vents 
&VENT TYPE = 'FLOOR' ID = 'scala S11' COMP_IDS = 'C6_C7_W_P3', 'C6_C7_P2_4' AREA = 3, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 900 F = 1, 1 OFFSETS = 6, 5.5 /
&VENT TYPE = 'FLOOR' ID = 'scala S10' COMP_IDS = 'C8_W_P3', 'C8_W_P2' AREA = 3, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 900 F = 1, 1 OFFSETS = 1, 4.85 /
&VENT TYPE = 'FLOOR' ID = 'scala S7' COMP_IDS = 'Comp 1', 'Comp 2' AREA = 3, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 900 F = 1, 1 OFFSETS = 6, 4.85 /
&VENT TYPE = 'FLOOR' ID = 'scala S6' COMP_IDS = 'Comp 3', 'Comp 4' AREA = 3, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 900 F = 1, 1 OFFSETS = 1, 4.85 /
&VENT TYPE = 'FLOOR' ID = 'scala S5' COMP_IDS = 'Comp 5', 'Comp 6' AREA = 3, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 900 F = 1, 1 OFFSETS = 6, 4.85 /
&VENT TYPE = 'FLOOR' ID = 'scala S4' COMP_IDS = 'Comp 7', 'Comp 8' AREA = 3, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 900 F = 1, 1 OFFSETS = 1, 4.85 /
&VENT TYPE = 'FLOOR' ID = 'scala S1' COMP_IDS = 'Comp 21', 'Comp 17' AREA = 2, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 900 F = 1, 1 OFFSETS = 1.5, 0.45 /
&VENT TYPE = 'FLOOR' ID = 'scala S2' COMP_IDS = 'Camino S2', 'Scala S2' AREA = 2, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 900 F = 1, 1 OFFSETS = 1.5, 0.45 /
&VENT TYPE = 'CEILING' ID = 'Cupolino S2' COMP_IDS = 'OUTSIDE', 'Camino S2' AREA = 2, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 59, 60 F = 0, 0, 1 OFFSETS = 1.5, 0.45 /
&VENT TYPE = 'CEILING' ID = 'Cupolino C8' COMP_IDS = 'OUTSIDE', 'C8_C_P3' AREA = 2, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 59, 60 F = 0, 0, 0.18 OFFSETS = 1.5, 0.45 /
&VENT TYPE = 'CEILING' ID = 'Cupolino C7' COMP_IDS = 'OUTSIDE', 'C6_C7_C' AREA = 2, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 59, 60 F = 0, 0, 0.18 OFFSETS = 3.5, 0.45 /
&VENT TYPE = 'CEILING' ID = 'Cupolino C6' COMP_IDS = 'OUTSIDE', 'C6_C7_C' AREA = 2, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 59, 60 F = 0, 0, 0.18 OFFSETS = 10.5, 0.45 /
&VENT TYPE = 'CEILING' ID = 'Cupolino C5' COMP_IDS = 'OUTSIDE', 'Comp 9' AREA = 2, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 59, 60 F = 0, 0, 0.18 OFFSETS = 3.5, 0.45 /
&VENT TYPE = 'CEILING' ID = 'Cupolino C4' COMP_IDS = 'OUTSIDE', 'Comp 10' AREA = 2, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 59, 60 F = 0, 0, 0.18 OFFSETS = 3.5, 0.45 /
&VENT TYPE = 'CEILING' ID = 'Cupolino C3' COMP_IDS = 'OUTSIDE', 'Comp 11' AREA = 2, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 59, 60 F = 0, 0, 0.18 OFFSETS = 3.5, 0.45 /
&VENT TYPE = 'CEILING' ID = 'Cupolino C2' COMP_IDS = 'OUTSIDE', 'Comp 12' AREA = 2, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 59, 60 F = 0, 0, 0.18 OFFSETS = 3.5, 0.45 /
&VENT TYPE = 'CEILING' ID = 'Cupolino C1' COMP_IDS = 'OUTSIDE', 'Comp 21' AREA = 2, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 59, 60 F = 0, 0, 1 OFFSETS = 1.5, 0.45 /
&VENT TYPE = 'CEILING' ID = 'velux 19' COMP_IDS = 'OUTSIDE', 'Comp 19' AREA = 1, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 OFFSETS = 3.5, 4.85 /
&VENT TYPE = 'CEILING' ID = 'velux 7' COMP_IDS = 'OUTSIDE', 'Comp 7' AREA = 2, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 OFFSETS = 3.5, 4.85 /
&VENT TYPE = 'CEILING' ID = 'velux 5' COMP_IDS = 'OUTSIDE', 'Comp 5' AREA = 2, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 OFFSETS = 3.5, 4.85 /
&VENT TYPE = 'CEILING' ID = 'velux 3' COMP_IDS = 'OUTSIDE', 'Comp 3' AREA = 2, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 OFFSETS = 3.5, 4.85 /
&VENT TYPE = 'CEILING' ID = 'velux 1' COMP_IDS = 'OUTSIDE', 'Comp 1' AREA = 2, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 OFFSETS = 3.5, 4.85 /
&VENT TYPE = 'CEILING' ID = 'velux 22' COMP_IDS = 'OUTSIDE', 'Comp 22' AREA = 4, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 OFFSETS = 3.5, 4.85 /
&VENT TYPE = 'CEILING' ID = ' velux 23' COMP_IDS = 'OUTSIDE', 'Comp 23' AREA = 4, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 OFFSETS = 3.5, 4.85 /
&VENT TYPE = 'CEILING' ID = 'velux 24' COMP_IDS = 'OUTSIDE', 'Comp 24' AREA = 4, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 OFFSETS = 3.5, 4.85 /
&VENT TYPE = 'CEILING' ID = 'velux 25' COMP_IDS = 'OUTSIDE', 'Comp 25' AREA = 4, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 OFFSETS = 3.5, 4.85 /
&VENT TYPE = 'CEILING' ID = 'velux 26' COMP_IDS = 'OUTSIDE', 'Comp 26' AREA = 1, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 OFFSETS = 3.5, 4.85 /
&VENT TYPE = 'CEILING' ID = 'velux C6_C7_P3_1' COMP_IDS = 'OUTSIDE', 'C6_C7_E_P3' AREA = 2, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 OFFSETS = 3.5, 5.5 /
&VENT TYPE = 'CEILING' ID = 'velux C6_C7_P3_2' COMP_IDS = 'OUTSIDE', 'C6_C7_E_P3' AREA = 2, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 OFFSETS = 10.5, 5.5 /
&VENT TYPE = 'CEILING' ID = 'velux C6_C7_P3_3' COMP_IDS = 'OUTSIDE', 'C6_C7_E_P3' AREA = 4, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 OFFSETS = 3.5, 17.5 /
&VENT TYPE = 'CEILING' ID = 'velux C6_C7_P4_4' COMP_IDS = 'OUTSIDE', 'C6_C7_E_P3' AREA = 4, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 OFFSETS = 10.5, 17.5 /
&VENT TYPE = 'CEILING' ID = 'velux C8_W' COMP_IDS = 'OUTSIDE', 'C8_W_P3' AREA = 4, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 OFFSETS = 3.5, 4.85 /
&VENT TYPE = 'CEILING' ID = 'velux C8_E' COMP_IDS = 'OUTSIDE', 'C8_E_P3' AREA = 4, SHAPE = 'SQUARE' 
      CRITERION = 'TIME' T = 0, 89, 90 F = 0, 0, 0.18 OFFSETS = 3.5, 4.85 /
 
!! Fires 
&FIRE ID = 'New Fire'  COMP_ID = 'C6_C7_P2_4', FIRE_ID = 'New Fire'  LOCATION = 7, 3 / 
&CHEM ID = 'New Fire' CARBON = 40.1238 CHLORINE = 0.0619 HYDROGEN = 68.1857 NITROGEN = 0.018 OXYGEN = 29.6 HEAT_OF_COMBUSTION = 20000 RADIATIVE_FRACTION = 0.35 / 
&TABL ID = 'New Fire' LABELS = 'TIME', 'HRR' , 'HEIGHT' , 'AREA' , 'CO_YIELD' , 'SOOT_YIELD' , 'HCN_YIELD' , 'HCL_YIELD' , 'TRACE_YIELD'  /
&TABL ID = 'New Fire', DATA = 0, 0, 0, 0.1, 0.1, 0.07, 0.15, 0.01, 0 /
&TABL ID = 'New Fire', DATA = 60, 10, 0, 0.15, 0.1, 0.07, 0.15, 0.01, 0 /
&TABL ID = 'New Fire', DATA = 120, 40, 0, 0.2, 0.1, 0.07, 0.15, 0.01, 0 /
&TABL ID = 'New Fire', DATA = 180, 90, 0, 0.25, 0.1, 0.07, 0.15, 0.01, 0 /
&TABL ID = 'New Fire', DATA = 240, 160, 0, 0.3, 0.1, 0.07, 0.15, 0.01, 0 /
&TABL ID = 'New Fire', DATA = 328.633, 300, 0, 0.35, 0.1, 0.07, 0.15, 0.01, 0 /
&TABL ID = 'New Fire', DATA = 360, 300, 0, 0.4, 0.1, 0.07, 0.15, 0.01, 0 /
&TABL ID = 'New Fire', DATA = 420, 300, 0, 0.45, 0.1, 0.07, 0.15, 0.01, 0 /
&TABL ID = 'New Fire', DATA = 480, 300, 0, 0.5, 0.1, 0.07, 0.15, 0.01, 0 /
&TABL ID = 'New Fire', DATA = 540, 300, 0, 0.55, 0.1, 0.07, 0.15, 0.01, 0 /
&TABL ID = 'New Fire', DATA = 600, 300, 0, 0.6, 0.1, 0.07, 0.15, 0.01, 0 /
&TABL ID = 'New Fire', DATA = 660, 300, 0, 0.65, 0.1, 0.07, 0.15, 0.01, 0 /
&TABL ID = 'New Fire', DATA = 720, 300, 0, 0.7, 0.1, 0.07, 0.15, 0.01, 0 /
&TABL ID = 'New Fire', DATA = 780, 300, 0, 0.75, 0.1, 0.07, 0.15, 0.01, 0 /
&TABL ID = 'New Fire', DATA = 840, 300, 0, 0.8, 0.1, 0.07, 0.15, 0.01, 0 /
&TABL ID = 'New Fire', DATA = 900, 300, 0, 0.85, 0.1, 0.07, 0.15, 0.01, 0 /
 
!! Devices
&DEVC ID = 'Pav 1' COMP_ID = 'Comp 6' LOCATION = 3.5, 1.7, 0 TYPE = 'PLATE' MATL_ID = 'STR 6'  NORMAL = 0, 0, 1 TEMPERATURE_DEPTH = 0.01 /
&DEVC ID = 'Pav 2' COMP_ID = 'Comp 6' LOCATION = 3.5, 5, 0 TYPE = 'PLATE' MATL_ID = 'STR 6'  NORMAL = 0, 0, 1 TEMPERATURE_DEPTH = 0.01 /
&DEVC ID = 'Pav 3' COMP_ID = 'Comp 6' LOCATION = 3.5, 8.3, 0 TYPE = 'PLATE' MATL_ID = 'STR 6'  NORMAL = 0, 0, 1 TEMPERATURE_DEPTH = 0.01 /
&DEVC ID = 'HeatDetector_1' COMP_ID = 'Comp 6' LOCATION = 3.5, 1.7, 2.57 TYPE = 'HEAT_DETECTOR' SETPOINT = 50, RTI = 5 /
&DEVC ID = 'HeatDetector_2' COMP_ID = 'Comp 6' LOCATION = 3.5, 5, 2.57 TYPE = 'HEAT_DETECTOR' SETPOINT = 50, RTI = 5 /
&DEVC ID = 'HeatDetector_3' COMP_ID = 'Comp 6' LOCATION = 3.5, 8.3, 2.57 TYPE = 'HEAT_DETECTOR' SETPOINT = 50, RTI = 5 /
&DEVC ID = 'SmokeDetect_1' COMP_ID = 'Comp 6' LOCATION = 3.5, 1.7, 2.57  TYPE = 'SMOKE_DETECTOR' SETPOINTS = 23.93346, 28 /
&DEVC ID = 'SmokeDetect_2' COMP_ID = 'Comp 6' LOCATION = 3.5, 6, 2.57  TYPE = 'SMOKE_DETECTOR' SETPOINTS = 23.93346, 28 /
&DEVC ID = 'SmokeDetect_3' COMP_ID = 'Comp 6' LOCATION = 3.5, 8.3, 2.57  TYPE = 'SMOKE_DETECTOR' SETPOINTS = 23.93346, 28 /
&DEVC ID = 'SmokeDetect_4' COMP_ID = 'Comp 4' LOCATION = 3.5, 6, 2.57  TYPE = 'SMOKE_DETECTOR' SETPOINTS = 23.93346, 28 /
 
!! Surface Connections
&CONN TYPE = 'WALL' COMP_ID = 'Comp 2'  COMP_IDS =   'C6_C7_P2_7'  'Comp 4'
      F = 0.5 0.5  /
&CONN TYPE = 'WALL' COMP_ID = 'Comp 4'  COMP_IDS =   'Comp 6'  'Comp 2'
      F = 0.5 0.5  /
&CONN TYPE = 'WALL' COMP_ID = 'Comp 6'  COMP_IDS =   'Comp 8'  'Comp 4'
      F = 0.5 0.5  /
&CONN TYPE = 'WALL' COMP_ID = 'Comp 8'  COMP_IDS =   'Comp 6'  'Comp 18'
      F = 0.5 0.5  /
&CONN TYPE = 'WALL' COMP_ID = 'Comp 18'  COMP_IDS =   'Comp 8' 'OUTSIDE'
      F = 0.5 0.5  /
&CONN TYPE = 'WALL' COMP_ID = 'Comp 22'  COMP_IDS =   'Comp 23'  'C6_C7_W_P3'
      F = 0.5 0.5  /
&CONN TYPE = 'WALL' COMP_ID = 'Comp 23'  COMP_IDS =   'Comp 22'  'Comp 24'
      F = 0.5 0.5  /
&CONN TYPE = 'WALL' COMP_ID = 'Comp 24'  COMP_IDS =   'Comp 23'  'Comp 25'
      F = 0.5 0.5  /
&CONN TYPE = 'WALL' COMP_ID = 'Comp 25'  COMP_IDS =   'Comp 24'  'Comp 26'
      F = 0.5 0.5  /
&CONN TYPE = 'WALL' COMP_ID = 'Comp 26'  COMP_IDS =   'Comp 25' 'OUTSIDE'
      F = 0.5 0.5  /
&CONN TYPE = 'FLOOR' COMP_ID = 'Comp 1' COMP_IDS = 'Comp 2' / 
&CONN TYPE = 'FLOOR' COMP_ID = 'Comp 3' COMP_IDS = 'Comp 4' / 
&CONN TYPE = 'FLOOR' COMP_ID = 'Comp 5' COMP_IDS = 'Comp 6' / 
&CONN TYPE = 'FLOOR' COMP_ID = 'Comp 7' COMP_IDS = 'Comp 8' / 
&CONN TYPE = 'FLOOR' COMP_ID = 'Comp 19' COMP_IDS = 'Comp 18' / 
&CONN TYPE = 'FLOOR' COMP_ID = 'Comp 22' COMP_IDS = 'Comp 27' / 
&CONN TYPE = 'FLOOR' COMP_ID = 'Comp 23' COMP_IDS = 'Comp 28' / 
&CONN TYPE = 'FLOOR' COMP_ID = 'Comp 24' COMP_IDS = 'Comp 29' / 
&CONN TYPE = 'FLOOR' COMP_ID = 'Comp 25' COMP_IDS = 'Comp 30' / 
&CONN TYPE = 'FLOOR' COMP_ID = 'Comp 26' COMP_IDS = 'Comp 31' / 
 
!! Visualizations
&SLCF COMP_ID = 'Comp 6' DOMAIN = '2-D'  POSITION = 3.5, PLANE = 'X' / 
&SLCF COMP_ID = 'Comp 6' DOMAIN = '2-D'  POSITION = 6, PLANE = 'Y' / 
&SLCF COMP_ID = 'Comp 6' DOMAIN = '2-D'  POSITION = 1.8, PLANE = 'Z' / 
