So, a bit unprepared, I called in and found water was doing a rapid
dribble from the overflow (I was expecting either a drip or it to be
I couldn't see much in the loft (only had a small torch from the car)
but after removing the insulation it seems that the tank is sitting in
(or perhaps it's part of it?) a drip tray and it was the drain from
the drip tray that was dribbling outsite. This drain also explains
why there were three overflow / warning pipes, which threw me
Seems a great idea having a drip tray, pity that seems to have
partially failed too, as some water had gone through the ceiling,
although it would have been much worse without it. Are these trays
routinely fitted - my house certainly hasn't got one?
I'm not sure of the age of Mum's house - either just before or just
after the 2nd WW I would guess. The bathroom and toilet water is fed
from the tank (as well the hot, obviously). Is the pipework from the
tank (there are two outlet connections) likely to be steel?
To be honest, if you have a leaking galvanised tank in an attic it is
probably well overdue for replacement.
Drip trays are (in my view) a good idea, I now have both a shower pump and a
domestic hot water pump mounted in them (after suffering a seal failure).
They are not common, especially for big tanks. Sounds like it may have been
put in after an earlier leak was patched.
and do this before probing around the tank - it might be very fragile
and almost ready to lose a large flake of metal, allowing all the
water to gush out.
Make sure the boiler isn't going to fire up if the water supply to a
header/vent tank is switched off.
> To be honest, if you have a leaking galvanised tank in an attic it is
> probably well overdue for replacement.
> Drip trays are (in my view) a good idea, I now have both a shower pump and a
> domestic hot water pump mounted in them (after suffering a seal failure).
> They are not common, especially for big tanks. Sounds like it may have been
> put in after an earlier leak was patched.
I've only ever seen one, and it was under a hot water cylinder.
[email address is not usable -- followup in the newsgroup]
I'll second that I have seen it happen twice.
1st time I was fitting a cable for an electric shower. As I passed the cable
up through the ceiling in the airing cupboard I hit the galvanised tank. The
bottom of the tank just fell off. That cost me a few quid.
The second was when I replaced a CH system. The tank was drained and as soon
as I touched the ballcock it fell off leaving a big hole in the tank.
I'm fairly sure the drip tray was part of the tank, but whether it
really is a tray, or just a lip runing around the base of the tank, I
couldn't tell. It had its own drain though, and without it the house
would have suffered considerable damage. Pity that it still allowed
some water to drip into the house though.
Any idea what the pipework from the tank to the hot/cold will be
(house is, I think, between the wars) - would it be steel, copper or
"Rory" <Rory...@hotmail.com> wrote in message
My guess would be steel. The rising main might be lead, but probably not
stuff in the house.
Any of the above, although it might be wrought iron, rather than steel,
which makes no practical difference. The only way to know for sure is to
What I'd described as a tray was actually a sheet of lead laid over a
frame, with a drain hole and a lead overflow pipe soldered into it.
Frustrating that it had leaked, but couldn't see where.
The old tank just looked horrendous inside, with massive and thick
"growths" on the walls. There were at least a couple of rusty spots on
the outside, where water had been seeping through.
Apart from the drain for the tray and the tank overflow which were
both lead, the plumber reckoned the other pipework was very heavy duty
He'd turned up with a big tank, but it was an inch out from going
through the loft hatch. This strikes me as daft - many hatches are
probably nominally 2ft square but in reality end up a bit less. Why
not make the tanks an inch or two smaller so you'd be sure they'll go
in? Then you wouldn't have to faff about with 2 tanks.
He had a heck of a job getting rid of the airlocks from the domestic
hot water - that would probably have defeated me without his range of